Payment & Shipping Terms:
|Material:||SUS 304，201，202||HEPA Filter:||H13， H14|
|UV Light:||Philips||Qty Of Nozzle:||4|
|AIR FLOW(m/s):||0.45m/s / 22 M/s||CLEAN CLASS:||ISO CLASS 5|
Clean laminar flow Laboratory clean transfer wind Pass Box Pass Through Window with CE UL for pharmaceutical factory
The stainless steel clean room pass box adopts the SUS304 stainless steel as the material for interior and exterior product body and the two doors. The thickness of the stainless steel is 1.0mm. Meanwhile, the product is equipped with the Taihu ultraviolet lamp with the power of 10W and the wavelength of 254nm. It can get the ideal sterilization effect. In addition, the embedded type installation of ultraviolet lamp can reduce the contact possibility of delivered articles and ultraviolet lamp tube to ensure safe use.
By taking electronic interlocking, the two doors of the stainless steel clean room pass box cannot be opened at the same time. The adopted lock is the high strength magnetic lock. It can bear the load of 60kg. The two doors of the product are set with transparent visible observation windows with round corners. They are flat and smooth without welding spot. The embedded design makes the doors and the body of the product at the same plane. The PVC plastic sealing strip is also available with good sealing performance. The soft contact control type switches of the two doors control the door lock and ultraviolet lamp respectively. Meanwhile, the bottom corners of the interior of the product are designed with the arc of 45 degrees. With a nice interior available, the product can be cleaned easily. In addition, a matched ultraviolet lamp tube can be provided with the product for free.
The UVC wave band can also be called shortwave sterilizing ultraviolet. Its wavelength ranges from 200 to 275nm. The UVC wave band has the weakest penetrability and cannot penetrate most of the transparent glass and plastic. The shortwave ultraviolet in the sunlight is almost absorbed by the ozonosphere completely. It has great harm to the human body. Short time irradiation can burn the skin. And long-term or high-intensity irradiation can cause skin cancer. The ultraviolet lamp can emit the UVC shortwave ultraviolet. So the operator should know that the ultraviolet lamp can be opened only after the doors of the pass box have been closed tightly to avoid harm.
1. Outer and Inner Dimension. The outer dimension should be decided according to clean room design, while the inner dimension is for the operation area.
2. The dynamic passbox is suit for the transmission happened from lower cleanliness environment to higher cleanliness environment. If the transmission happens between same cleanliness, static passbox is recommended.
3. The direction of door opening should be considered according to the position of passbox.4. SUS 304 is recommended for the casing of passbox.
|OUTTER SIZE(W x D x H)||760 x 660 x 1350 mm|
|INNER SIZE(W x D x H)||600 x 600 x 800 mm|
|CLEAN CLASS||ISO CLASS 5 (100)|
|AIR FLOW(m/s)||0.45m/s / 22 m/s|
|qty of nozzle||4|
|air shower time(s)||12 Second(0-99Second could changable)|
|efficiency||H13 HEPA filter G4 Pre-Filter|
|Medium||Hepa Filter: Mini Pleated fiberglass:|
|Power Supply||220V AC 1PH 50 Hz|
|G.W. (kg )||274 kg|
|N.W.(kg )||150 kg|
|SIZE(LxWxH,mm)||920 x 850 x 1580 mm|